SMA requested MidNite Solar to design and build these DLTL combiners. There are 4 strings entering the combiner with 2 separate strings out. Specifically designed for the new dual channel MPPT on the transformer-less inverters.
4 strings into the combiner with 2 separate 30 amp strings out. Specifically designed for the new dual channel MPPT on the transformer-less inverters. This configuration will break the Positive and Negative of 2 separate 600vdc strings.
The difference between the regular Disco combiner and the DLTL version is that the MNPV8HV-Disco-4X is made for a single 8 string inverter, 2 4 sting inverters or one 4 string transformerless where as the DLTL is set up for 4 strings in and 2 strings out for Dual MPPT on transformerless
Rapid system shutdown compliant
Type 4X aluminum enclosure (No Rust)
Number of Fuse Holders - 8
Current Rating - 60A
Max. Output Wire Size - 2/0
Output Circuits - 2
90 degree C connections
1/2 strain reliefs included
Meets 2014 NEC 690.12
See through dead front and color coded bus bar guards
Fuses and fuse holders included
Warranty - 5 yrs.
#10 AWG internal wiring
Available with Power Supply board factory installed for Plug and Play compatibility with the MidNite Solar Birdhouse Rapid System Shut Down Controller.
MNPV8HV-DLTL 4X-PSB $1,039.00